The information below comes from the statement of deficiencies compiled by health inspectors and provided to AHCJ by the Centers for Medicare and Medicaid Services. It does not include the steps the hospital plans to take to fix the problem, known as a plan of correction. For that information, you should contact the hospital, your state health department or CMS. Accessing the document may require you to file a Freedom of Information Request. Information on doing so is available here.
|CRYSTAL CLINIC ORTHOPAEDIC CENTER||444 NORTH MAIN STREET AKRON, OH 44310||Oct. 17, 2017|
|VIOLATION: PHYSICAL ENVIRONMENT||Tag No: A0700|
|Based on observation, interview, and documentation review the facility failed to ensure the building vertical openings complied with NFPA 101, duct detectors and heat detectors complied with NFPA 72, and damper testing and replacement complied with NFPA 80 and 90a (A710). This has the potential to affect all patients receiving services from the facility. The cumulative effects of these systemic practices resulted in the facility's inability to ensure the safety of patients. The facility's census was 0.|
|VIOLATION: LIFE SAFETY FROM FIRE||Tag No: A0710|
|Based on observation, interview, and documentation review, the facility failed to meet the requirements for life safety, specifically, the applicable provisions of the 2012 edition of the Life Safety Code of the National Fire Protection Association. This had the potential to affect all patients receiving services from the facility. The facility census was 0.
1. Please see K311 for findings related to the facility failing to ensure vertical chases were free of penetrations.
2. Please see K345 for findings related to the facility failing to ensure sensitivity testing was completed on duct detectors and testing was completed on all heat detectors.
3. Please see K521 for findings related to the facility failing to ensure damper testing and repair/replacement was completed.