The information below comes from the statement of deficiencies compiled by health inspectors and provided to AHCJ by the Centers for Medicare and Medicaid Services. It does not include the steps the hospital plans to take to fix the problem, known as a plan of correction. For that information, you should contact the hospital, your state health department or CMS. Accessing the document may require you to file a Freedom of Information Request. Information on doing so is available here.
|NORTHERN LIGHT MAYO HOSPITAL||897 WEST MAIN STREET DOVER FOXCROFT, ME 04426||Jan. 10, 2018|
|VIOLATION: Fire Alarm System - Installation||Tag No: K0341|
|Based on observation and interview by surveyors and on 01/10/2018:
The fire alarm system was in trouble at the fire panel. The trouble is a ground fault somewhere in the system and has been in trouble since the panel was installed in July of 2017.
The pull station in zone 4 Ambulance entrance did not work when pulled.
The Lead Maintenance Engineer and facility electrician were present during this observation