The information below comes from the statement of deficiencies compiled by health inspectors and provided to AHCJ by the Centers for Medicare and Medicaid Services. It does not include the steps the hospital plans to take to fix the problem, known as a plan of correction. For that information, you should contact the hospital, your state health department or CMS. Accessing the document may require you to file a Freedom of Information Request. Information on doing so is available here.
|BLAKE MEDICAL CENTER||2020 59TH ST W BRADENTON, FL 34209||July 18, 2019|
|VIOLATION: Electrical Systems - Essential Electric Syste||Tag No: K0918|
|Based on record review and interview, with the Director of Plant Operations, the facility failed to maintain the transfer switch gear.
During facility record review with the Director of Plant Operations, it was revealed that during the scheduled maintenance by the facility's vendor on 09/05/2018, it was documented that transfer switch ATS-EQB control panel had been recommended to be replaced in the near future. It was also documented that transfer switch ATS-9(EA) caused major damage to equipment years ago when bypassed and had never been repaired. An interview was conducted with the Director of Plant Operations concurrent with observations and confirmed the findings.
per NFPA 101 (2012 Edition) 4.5.8
per NFPA 99 (2012 Edition) 126.96.36.199.1.3
per NFPA 110 (2010 Edition) 8.3.5